**Surge Impedance Loading (SIL)**is the most important parameter for determining the maximum loading capacity (MW loading) of transmission lines. Before understanding SIL in detail, first, we have to understand the concept of Surge and

**Surge impedance (Zs)**and its physical significance. So let’s discuss the topic in detail.

**What is Surge Impedance (Zs)?**

*per unit length*

*series impedance (z) per unit length. Then the*

**Characteristic impedance (Zc) of any lossless transmission line is defined as the square root of**

**(z/y).**

**z = R + jwL**and

**y = G + jwC.**

If we put the value of **z** and **y** in the definition of (**Zc**), then we find that Characteristic Impedance is a complex quantity. However, for lossless transmission lines (R=0 and G= 0)

**z = jwL**and

**y = jwC.**

according to the definition, Characteristic Impedance (Zc) is calculated as:

**Characteristic Impedance (Zc) = square root of (jwL/jwC).**

**Zs= Zc = square root of (L/C).**

**Surge impedance**of the line. When a purely resistive load of value equal to surge impedance is connected at the

receiving end of the line, then the reactive power generated by the shunt capacitor will be completely absorbed by the series inductor of the

transmission line.

The value of Surge impedance for overhead transmission line is around 400 ohm, whereas surge impedance value for underground cable is around 40 ohm.

**Significance of Surge impedance**

The significance of surge impedance is that if a pure resistance load that is equal to the surge impedance is connected to the end of the line with no resistance, a voltage surge introduced by the shunt capacitor to the sending end of the line would be completely absorbed by the series inductance at the receiving end of the transmission line.

**Surge impedance (Zs)**is a technical term that is used mostly in Electrical science in connection with the

**Surges on transmission lines**which may appear due to switching or lightning operation in our Electrical power system.

**What happens if the line terminates in surge impedance?**

**infinite line or**

**flat line**.

- There will not be any reflection of forwarding traveling waves and hence there will be no standing wave in the line. Therefore, the voltage will be the same throughout the line. Hence, in this case, the receiving end and sending end voltage will be the same.
- The line will compensate itself. That is, the reactive power demanded by the series inductance of the line will be supplied by the shunt capacitance. That’s why there will be no voltage drop (due to series inductance) and also no voltage boost (due to shunt capacitance).
- The load, as seen by the generator, is a pure resistance that will be equal to characteristic impedance. Hence the line is observed as equivalent to a pair of wires with zero resistance.

**Surge impedance loading (SIL) and its significance**.

**What is Surge impedance loading (SIL)?**

- Thermal limitation (I
^{2}R Limitation) - Voltage regulation
- Stability limitation

So in context to these limitations **Surge impedance loading (SIL)** is an important parameter in electrical science to predict the maximum loading capacity of any transmission line. It is the maximum MW loading of the transmission line at which reactive power balance occurs.

**SIL is defined as the maximum load (at unity power factor) that can be delivered by the transmission line when the loads terminate with a value equal to surge impedance (Zs) of the line.**Simply if any line terminates with surge impedance then the corresponding loading in MW is known as Surge Impedance Loading (SIL).

In other words, we can define surge impedance loading (SIL) as

**SIL is the maximum load connected in the transmission line for which total reactive power generated (Capacitive VAR) is equal to total reactive power consumed (Inductive VAR)**. So as to maintain an exact balance of reactive power consumption (by series inductance of line) and generation (by shunt capacitance of line). That’s why the net flow of reactive power in the transmission line will be zero and hence transmission line is assumed to be loaded as purely resistive load.

**SI unit of surge impedance loading (SIL) is Mega-Watt (MW).**

Mathematically SIL is expressed as:

SIL (in MW) = (Square of line voltage in kV)/(Surge impedance in ohm)

**Calculation of Surge impedance loading (SIL)**

As we know long transmission lines (length > 250 km) are represented by the distributed parameter model. In this model, the capacitance and inductance are distributed uniformly along the line. When the line is charged then the shunt capacitance generates reactive power and feeds to the line while the series inductance absorbs the reactive power. Hence voltage drop occurs in line due to series, inductance is compensated by the shunt capacitance of the line.

If we take a balance of reactive powers due to inductance and capacitance then we get an expression as:

Here the quantity having a dimension of resistance is surge impedance denoted by the symbol Zs. It is considered as a purely resistive load which when connected at the receiving end of the transmission line, then the reactive power generated by shunt capacitance will be completely absorbed by the series inductance of the line.

**surge impedance**(Zs) value in the above mathematical formula of SIL is expressed as:

SIL (in MW) = (Square of line voltage in kV)/(Surge impedance in ohm)

**Effect of Surge Impedance Loading (SIL)**

From the above expression of SIL we observed that SIL depends on the line voltage at the receiving end. Normally a line is loaded above SIL for better utilization of the conductor. In other words, we can say that SIL should always be less than the maximum loading capacity of the line.

When the line is loaded less than its SIL, then it acts like a shunt capacitor which means it will supply MVAR to the system. In this case, the receiving end voltage will be greater than sending end voltage. In such a case line has to be compensated with an inductor to bring down the voltage to a normal level. However when the line is loaded above its SIL, then it acts like a shunt reactor that will absorb MVAR from the system. In such a case voltage drop occurs in the line, due to this receiving end voltage will be smaller than the sending end voltage. Hence a compensator is required to maintain the voltage level.

**If the loading is equal to SIL, then the voltage profile of the line is Flat.****If the loading is greater than SIL, then the line has an inductive nature.****If the loading is less than SIL, then the line has a capacitive nature**.

**How to improve surge impedance loading?**

**Electrical power**through a transmission line can be either increased by increasing the value of the receiving end line voltage (V

_{LL}) or by reducing the value of surge impedance (Z

_{s}).

Since Voltage transmission capability is increasing day by day. So the most commonly adopted method for increasing the power limit of the heavily loaded transmission line is by increasing the voltage level. However, there is a limit beyond which it is neither economical nor practical to increase the receiving end line voltage of the power network.

**surge impedance**

**(Z**

_{s}**)**or characteristics impedance of the transmission line, we can easily improve its surge impedance loading (SIL).

Since surge impedance is directly proportional to inductance and inversely proportional to the capacitance. Hence the value of surge impedance can be reduced * either* by increasing the capacitor (C) of the line

**by decreasing the inductance (L) of the line. However, the inductance of the line cannot be reduced easily.**

*or***Using series capacitor:**By the use of a series capacitor surge impedance and phase shift get reduced due to a decrease in inductance value (L). It also improves system stability. This capacitor also helps in reducing the line voltage drop. But the main problem with this method is It causes difficulty under the short circuit condition as a series capacitor will get damaged.**Using a shunt capacitor:**Also by the use of a shunt capacitor surge impedance is reduced but the phase shift of the system increases. This affects the poor stability of the system especially when the synchronous machines are present in the load. So this method is not feasible where the stability limit is the main concern in the power system.

Hence surge impedance loading of line is increased by using either series capacitor or shunt capacitor in the transmission line. But practically series capacitor is a more feasible and effective method for improving the SIL of a line.

**Read More Article**